The Ecodesign Lot 15 means regulations regarding particulate matter in combination with energy efficiency and NOx and COx.
In order to be able to compare parameters with gas boilers (lot 1), the Gross Calorific Value, GCV, is used when measuring energy efficiency.
The regulations are only valid for new installations from 1/1 2020.
Initially, the regulations cover boilers up to 500kW, but will eventually also include boiler up to 1000kW.
Most existing boiler systems can be fitted with a FGR®. The combined system of burner, boiler and FGR® will fulfill and exceed the Ecodesign requirements!
|Parameter||Valid from 2020|
|Seasonal space heating energy efficiency||77% for boilers larger than 20 kW, 75% for boilers smaller than 20 kW|
|Emission of particulate matter||Automatically fed: 40 mg/m³, Manually fed: 60 mg/m³,|
|OGC (Organic Gaseous Compounds) (10% O2)||Automatically fed: 20 mg/m³, Manually fed: 30 mg/m³|
|Carbon monoxide (CO) (10% O2)||Automatically fed: 500 mg/m³, Manually fed: 700 mg/m³|
|Nitrogen oxides (NOx) (10% O2)||Bio fuel: 200 mg/m³, Fossil fuel: 350 mg/m³|
Source: Swedish Energy Agency